Standards/Guidelines for control of
Noise Pollution from Stationary Diesel Generator (DG) Sets.
||Noise Standards for DG Sets (15-500 KVA)
The total sound power level, Lw, of a DG
set should be less than, 94+10 log10 (KVA), dB(A), at the manufacturing stage,
where, KVA is the nominal power rating of a DG set.
This level should fall by 5 dB(A) every five years, till 2007, i.e. in 2002 and then in
||Mandatory acoustic enclosure/acoustic treatment of room
for stationary DG sets (5 KVA and above)
Noise from the DG set should be controlled
by providing an acoustic enclosure or by treating the room acoustically.
The acoustic enclosure/acoustic treatment of the room should be designed for minimum 25
dB(A) Insertion Loss or for meeting the ambient noise standards, which ever is on the
higher side (if the actual ambient noise is on the higher side, it may not be possible to
check the performance of the acoustic enclosure/acoustic treatment. Under such
circumstances the performance may be checked for noise reduction upto actual ambient noise
level, preferably, in the night time). The measurement for Insertion Loss may be
done at different points at 0.5m from the acoustic enclosure/room, and then averaged.
The DG set should also be provide with proper exhaust muffler with Insertion Loss of
minimum 25 dB(A).
||Guidelines for the manufacturers/users of DG sets (5 KVA
The manufacturer should offer to the user
a standard acoustic enclosure of 25 dB(A) Insertion Loss and also a suitable exhaust
muffler with Insertion Loss of 25 dB(A).
||The user should make efforts to bring down the noise levels
due to the DG set, outside his premises, within the ambient noise requirements by proper
siting and control measures.
The manufacturer should furnish noise
power levels of the unlicenced DG sets as per standards prescribed under (A)
The total sound power level of a DG set,
at the user's end, shall be within 2 dB(A) of the total sound power level of the DG set,
at the manufacturing stage, as prescribed under (A).
Installation of a DG set must be strictly
in compliance with the recommendation of the DG set manufacturer.
A proper routine and preventive
maintenance procedure for the DG set should be set and followed in consultation with the
DG set manufacturer which would help prevent noise levels of the DG set from deteriorating
Order of the Lt. Governor of Delhi in respect of D.G.
(5th December, 2001)
In exercise of the powers conferred by section 5 of the Environment (Protection) Act,
1986, (29 of 1986), read with the Government of India, Ministry of Home Affairs
notification S.O. 667 (E) bearing No. F.No. U-11030/J/91-VTL dated 10th September, 1992,
the Lt. Governor of Government of National Capital of Delhi hereby directs to all
owners/users of generators sets in the National Capital Territory of Delhi as follows :-
that generator sets above the capacity of
5 KVA shall not be operated in residential areas between the hours of 10.00 PM to 6.00 AM;
that the generator sets above the capacity
of 5 KVA in all areas residential/commercial/industrial shall operate only with the
mandatory acoustic enclosures and other standards prescribed in the Environment
(Protection) Rules, 1986;
that mobile generator sets used in social
gatherings and public functions shall be permitted only if they have installed mandatory
acoustic enclosures and adhere to the prescribed standards for noise and emission as laid
down in the Environment (Protection) Rules, 1986.
The contravention of the above directions shall make the offender
liable for prosecution under section 15 of the said Act which stipulates punishment of
imprisonment for a term which may extend to five years with fine which may extend to one
lakh rupees, or with both, and in case the failure of contravention continues, with
additional fine which may extend to five thousand rupees for every day during which such
failure or contravention continues after the conviction for the first such failure or
contravention and if still the failure or contravention continues beyond a period of one
year after the date of contravention, the offender continues beyond a period of one year
after the date of contravention, the offender shall be punishable with imprisonment for a
term which may extend to seven years.
Order Dated : 21st June, 2002
In exercise of the powers conferred by section 5 of the Environment (Protection) Act, 1986
(29 of 1986) read with the Govt. of India, Ministry of Home Affairs notifivation S.O.
667(E) bearing No. U-11030/J/91-VTL dated the 10th September, 1992, the Lt. Governor Govt.
of the National Capital Territory of Delhi hereby makes the following
amendment/modification in his order dated the 5th December, 2001 regarding the operation
of generator sets, namely:-
In the above said order, for clause(1), the following shall
be substituted, namely:-
"(1) that the generator stets above 5KVA shall not be operated in
residentoal areas between the hours from 10.00 p.m. to 6.00 a.m. except generator sets of
Group Housing Societies and Multi-storey residential apartments".